Money Supermarket.com – Ewloe Chester Installation March 2017 & Separate Installation January 2018
MoneySuperMarket.com is the UK’s leading and diversified price comparison website. They provide a place for consumers and providers to come together. They compare over 140 car insurance brands, more than 80 home insurance brands, over 60 credit card and personal loan providers, and 40 energy providers. They are able to do this by ensuring they are easy to use and transparent, putting the customers first.
MoneySuperMarket.com were looking to replace their current dated system with a more modern and efficient system. Enviro cool being a T7 approved warranty partner of Toshiba designed a Toshiba air conditioning system to suit the client’s needs.
We provided 7 four way blow ceiling cassettes to the 1st floor main office area running off 7 Digital Inverter outdoor condensing units which are designed to cope with up to -15 degree outdoor temperature and still deliver high level heating and cooling all year round. This system is A+ rated for energy consumption and runs on the latest none ozone depleting R410A gas.
An additional compact cassette was also installed into the office kitchen on a single split system.
The project began by de-commissioning … removing all refrigerant plant equipment and associated pipework, cable and drains. The new install began with a new main header being installed into the ceiling space which minimised clutter and gave the system a professional and neat layout.
Once the first fixing internally was complete we moved onto the positioning of the outdoor condensers which were all fitted inside a single protective cage. Condensers were lifted into place and piped up ready for commissioning.
The commissioning procedure is extremely important as the whole installation is pressure tested to 42bar for 1 hour and then 34bar for 24 hours to ensure there are no leaks on the system as the smallest leak impacts the environment and also affects the efficiency of the system. Both pressure tests passed on all units.
Once the condensers had been left energised overnight (to warm the oil in the compressors) it was time to switch on and check all is working as it should.
Commissioning sheets were filled out to validate the 7 year parts and labour warranty
The installation was then handed over to the client and demonstration was given to the appropriate staff members.
The works were completed ahead of schedule which the customer was pleased about. Passing comment on the quality of the installation and how tidy and non-disruptive the works were and that my engineers were a credit to our company.
Due to the quality of installation, MoneySuperMarket.com later chose Enviro cool to replace further units on the 1st floor.